Description: Due to the relocation of a magnet power supply, the installation of a buss, and an installation of chokes. and their need for cooling water a redesign of the Low Conductivity Water (LCW) system has been undertaken. This new system required the determination of an optimal pipe diameter for the High Bay pipe as well as the determination of the pressure drop and temperature rise in the buss. Based on numerous calculations it has been determined that the High Bay pipe should be 1 1/2 inch (1.90 O.D. x 1.610 I.D-40S steel). While the pressure drop in the buss was calculated to be 7.699 psi. Based on such a low pressure drop, no need for any additional pumps has presented itself. Finally, the temperature rise in the buss has been determined to be about 29.39 F for the Assembly Hall (route No.1). and 13.93 F for the Collision Hall (route No.2). The purpose of this engineering note is to explain the redesign of the low conductivity water system (LCW) at D-Zero. The areas to be covered include the sizing of the High Bay, the pressure drop and temperature rise in the buss. In addition, I will try to determine if any more pumps are needed to support this new system. Originally, the purpose of the LCW was to provide cooling for the EF, CF, SAMUS magnets and the magnet power supply. The water source is composed of two 1 1/2 BC, 20 hp, centrifugal pumps (see Table No.2) which are located in room 604 of the D-Zero Assembly building.
Date: October 15, 1996
Creator: Zaczek, Mariusz
Item Type: Refine your search to only Report
Partner: UNT Libraries Government Documents Department