Objectives of this program are to evaluate candidate alloys for Very High Temperature Reactor (VHTR) Nuclear Process Heat (NPH) and Direct Cycle Helium Turbine (DCHT) applications, in terms of the effect of simulated reactor primary coolant (helium containing small amounts of various other gases), high temperatures, and long time exposures, on the mechanical properties and structural and surface stability of selected candidate alloys. A second objective is to select and recommend materials for future test facilities and more extensive qualification programs. Work covered in this report includes the activities associated with the status of the simulated reactor helium supply system, testing equipment and gas chemistry analysis instrumentation and equipment. The progress in the screening test program is described: screening creep results and metallographic analysis for materials thermally exposed or tested at 750, 850, 950 and 1050/sup 0/C. Initiation of controlled purity helium creep-rupture testing in the intensive screening test program is discussed. In addition, the results of 1000-hour exposures at 750 and 850/sup 0/C on several experimental alloys are discussed.
This report is a technical evaluation of the final draft of the Fort St. Vrain (FSV) Upgraded Technical Specifications (UT/S) as issued by Public Service of Colorado (PSC) on May 27, 1988 with subsequent supplemental updates issued on June 15, 1988 and August 5, 1988. It has been compared for consistency, and safety conservatism with the Fort St. Vrain (FSV) Updated Final Safety Analysis Report (FSAR), the FSV Safety Evaluation Report (SER), the Facility Operating License, DPR-34, and all amendments to the Facility Operating License issued as of June 1, 1988, and Appendix A to the Operating License DPR-34, Technical Specifications. Because of the age of the plant, no supplements to the Fort St. Vrain SER have been issued since the original SER was not issued as a WASH or a NUREG report. This made it necessary to review all amendments to the Facility Operating License since they would contain the safety evaluations done to support changes to the Facility Operating License. The upgraded Fort St. Vrain Technical Specifications were also broadly compared with the latest Westinghouse Standard Technical Specifications (WSTS) to assure that what was proposed for Fort St. Vrain was consistent with the latest NRC staff practices for standard technical specifications.