Description: The Design Team continued to conference this quarter. Their primary task during this timeframe was to finalize the dryer design based on information learned from the NDIC Pilot work and detailed design discussions at Barr offices in August. Heyl-Patterson was tasked with incorporating all comments and drafting drawings. They submitted a preliminary proposal which spawned detailed discussions about tube bundle, air locks, and fire suppression systems. The type of fire protection specified dictated the final structural arrangement. Three meetings were spent discussing the pro's and con's of suppression vs. ventilation systems. In the end, the dryer and bucket elevator will have suppression systems and the remaining equipment will be explosion vented. This is in agreement with GRE's current insurer, FM Global. Three inlet airlocks were reduced to two and four outlets were reduced to three. The inlet plenum was subdivided for greater flexibility and sparging air added in the outlet plenum. It was also decided to use bundles with varied material, diameter, and tube & fin spacing. This will be completed in an effort to identify for us which configuration has the best heat transfer characteristics using coal as the fluidizing medium. The dryer will also be delivered in four pieces. This will allow for installation through the current access door on the Air Heater deck. The Input/Output list and functional description was completed and forwarded to Honeywell to finalize controls. Major pieces of equipment received this quarter were the Bucket Elevator, Liewell Screen, conveyors, and Motor Control Center. ICI completed removal of the wall separating Silo 28 from the dryer area; handrail and grating between the two areas has also been removed. They relocated a blowdown line. They moved an Air Heater basket access hatch.
Date: February 7, 2005
Creator: Bullinger, Charles
Item Type: Refine your search to only Report