Description: The acceptance test procedure (ATP) for the compressed air system at building 241-AW-273 was completed on March 11, 1993. The system was upgraded to provide a reliable source of compressed air to the tank farm. The upgrade included the demolition of the existing air compressor and associated piping, as well as the installation of a new air compressor with a closed loop cooling system. A compressed air cross-tie was added to allow the process air compressor to function as a back-up to the existing instrument air compressor. The purpose of the ATP was to achieve three primary objectives: verify system upgrade in accordance with the design media; provide functional test of system components and controls; and prepare the system for the Operational Test. The ATP was successfully completed with thirteen exceptions, which were resolved prior to completing the acceptance test. The repaired exceptions had no impact to safety or the environment and are briefly summarized. Testing ensured that the system was installed per design, that its components function as required and that it is ready for operational testing and subsequent turnover to operations.
Date: October 6, 1994
Creator: Kostelnik, A. J.
Item Type: Refine your search to only Report