D0 Silicon Upgrade: Lower Cleanroom Roof Quick Load Analysis Page: 2 of 9
This report is part of the collection entitled: Office of Scientific & Technical Information Technical Reports and was provided to Digital Library by the UNT Libraries Government Documents Department.
The following text was automatically extracted from the image on this page using optical character recognition software:
This engineering note documents calculations done to determine the
margin of safety for the lower clean room roof. The analysis was
done to give me a feeling of what the loads, stresses and capacity of
the roof is prior to installation and installation work to be done for
the helium refrigerator upgrade.
Ksults & Conclusion
The result of this quick look showed that the calculated loads
produce stress values and loads at about half the allowables. Based
on this result, I do not think that special precautions above personal
judgement are required for the installation work.
1.) Uniform floor loading of 50 lbs./ft^2 to account for rated capacity.
2.) Uniform floor loading of 3.1 lbs./ft^2 for the corrugated floor.
3.) Roof hatch weight of 28 lb/ft on support beams plus 3.1 lbs./ftA2
for the skin material. (Total weight used = 1360 lbs.)
4.) Dead weight of the W8 x 21 beams. (Actually used 28 lbs./ft in
5.) Dead weight of upgrade piping along south wall, 150 lbs. at each
support beam location. Total weight = 750 lbs.
S trsses/Load Capacities
Beams: Worst loaded beams are those to the east and west of the
hatch. This worst loaded beam was the only one analyzed. There
was a 3580 lb reaction at the north end of this beam and a 4700 lb
reaction at the south end. The highest bending moment was 241,275
in-lbs which results in a bending stress of 13.3 ksi. The allowable
bending stress per the AISC manual is 23.8 ksi. The shear stress was
not calculated but would be very low ( less than 3 ksi) compared to
the AISC manual allowable shear stress of 16.8 ksi.
Framed connection: A framed connection is used to attach beams
to beams and the beams to the wall. A 5 x 5 x 3/8" angle with two
3/4" dia. bolts are used on each side of the web. The allowable load
for this connection based on the bolts (which I assume are low
quality A307) is 17,700 lbs. The calculated load was 4700 lb.
Here’s what’s next.
This report can be searched. Note: Results may vary based on the legibility of text within the document.
Tools / Downloads
Get a copy of this page or view the extracted text.
Citing and Sharing
Basic information for referencing this web page. We also provide extended guidance on usage rights, references, copying or embedding.
Reference the current page of this Report.
Rucinski, Russ. D0 Silicon Upgrade: Lower Cleanroom Roof Quick Load Analysis, report, November 17, 1995; Batavia, Illinois. (digital.library.unt.edu/ark:/67531/metadc845557/m1/2/: accessed August 17, 2018), University of North Texas Libraries, Digital Library, digital.library.unt.edu; crediting UNT Libraries Government Documents Department.