Whitey SCHE Gauge and Root Valves Page: 1 of 20
This report is part of the collection entitled: Office of Scientific & Technical Information Technical Reports and was provided to Digital Library by the UNT Libraries Government Documents Department.
The following text was automatically extracted from the image on this page using optical character recognition software:
ENGINEERING CHANGE NOTICE - ------- -
Page 1 of r1J
2. ECN Category (mark one) 3. Originator's Name, Organization, MSIN, and Telephone No. 4. USQ Required? 5. Date
A. Artzer, CVDF, X3-78, 372-2801 [X] Yes  No 9/7/00
Direct Revision 6. Project Title/No./Work Order No. 7. Bldg./Sys./Fa. No. 8. Approval Designator
Change ECN  SNF/W-441, Spent Nuclear Fuel CVDF SNQ
Temporary  Cold Vacuum Drying 142K
Supersedure  9. Document Numbers Changed by this ECN 10. Related ECN No(s). 11. Related PO No.
Cancel/Void  (includes sheet no. and rev.)
SNF-3921, Rev. 5 N/A N/A
12a. Modification Work 12b. Work Package 12c. Modification Work Complete 12d. Restored to Original Condi-
No. tion (Temp. or Standby ECN only)
 Yes (fill out Blk. N/A N/A N/A
[X] No (NA Blks. 12b, Design Authority/Cog. Engineer Design Authority/Cog. Engineer
12c, 12d) Signature & Date Signature & Date
13a. Description of Change
13b. Design Baseline Document?  Yes [X] No
Revised Valve Seat Leakage Acceptance Criteria from <0. I SCC/min N2 @ 4000 psig to <0.1 SCC/min N2 @ 150 psig to match up with
operating conditions and OTE-2131 test procedure.
USQ Approval: C\/ 0 - - 5 A /"17 O
14a. Justification (mark one) 14b. Justification Details
Criteria Change  Seat leakage test is not needed at full design pressure because valves are open during normal operation.
Design Improvement [X]
EnvironyDenta  The design verification method for SC/SS components is by independent review in
Facility Deactivation 11 accordance with EN-6-027-01. Documentation of this review is accomplished by the
As-Found  independent review approval signature provided on page 2 of this ECN.
Facilitate Const [J
Const. Error/Omission 
15. Distribution (include name, MSIN, and no. of copies) RELEASE STAMP
See distribution sheet.
uTA. RELEASE ID:
Here’s what’s next.
This report can be searched. Note: Results may vary based on the legibility of text within the document.
Tools / Downloads
Get a copy of this page or view the extracted text.
Citing and Sharing
Basic information for referencing this web page. We also provide extended guidance on usage rights, references, copying or embedding.
Reference the current page of this Report.
Miska, C. R. Whitey SCHE Gauge and Root Valves, report, September 11, 2000; United States. (digital.library.unt.edu/ark:/67531/metadc740738/m1/1/: accessed September 20, 2018), University of North Texas Libraries, Digital Library, digital.library.unt.edu; crediting UNT Libraries Government Documents Department.