PUREX exhaust ventilation system installation test report Page: 59 of 80
This report is part of the collection entitled: Office of Scientific & Technical Information Technical Reports and was provided to Digital Library by the UNT Libraries Government Documents Department.
The following text was automatically extracted from the image on this page using optical character recognition software:
PUREX EXH SYSTEM ACCEPTANCE TEST PROCEDURE
6.3.118 De-energize the 24 Vdc test power supply.
6.3.119 Disconnect the Hall Effect limit switch test box from the EFl-3 outlet damper 2A
actuator terminals and re-land all lifted leads.
6.3.120 Lift the 24 Vdc supply wire for the actuator controller at terminal TS5-EF1-3-31.
6.3.121 Lift the 2.2 KQ "pull-up" (PU) resistor at terminal TS5-EFi-3-33.
6.3.122 Lift the 2.2 KQ "pull-up" (PU) resistor at terminal TS5-EF1-3-41.
6.3.123 Lift the 2.2 KQ "pull-up" (PU) resistor at terminal TS5-EF1-3-45.
6.3.124 Connect the Hall Effect limit switch test box test wire from TB-1 +24 Vdc to
6.3.125 Connect the Hall Effect limit switch test box test wire from TB-1 DC COM to
6.3.126 'Connect the Hall Effect limit switch test box as follows for testing limit switches
on the EFI-3 inlet damper 1B actuator:
- Terminals ZOS-CD-32-1B, TB-1 to TS5-EF1-3-34 for the left-hand
(RP1) extended limit switch.
- Terminals ZCS-CD-32-1B, TB-3 to TS5-EF1-3-38 for the left-hand
(RP1) retracted limit switch.
- Terminals ZOR-CD-32-1B, TB-6 to TS5-EF1-3-42 for the right-hand
(RP2) extended- limit switch.
" Terminals ZCR-CD-32-1B, TB-8 to TS5-EF1-3-46 for the right-hand
(RP2) retracted limit switch.
6.3.127 Ensure that the 24 Vdc test power supply is still connected to TB-9 (+)24 Vdc
and (-) DC Common on the Hall Effect limit switch test box.
6.3.128 Disconnect the CDI Test/Setup box from the EF1-3 outlet damper 2A actuator
terminals and re-land all lifted leads.
6.3.129 Lift the following leads in the SAMCONS Trailer at IR-9 and connect the CDI
Actuator Test/Setup box to the lifted leads:
- TB1-4, M+, Wire Tag # TS-CD-32-1B-2
- TB1-3, M-, Wire Tag # TS-CD-32-1B-1
DOCUMETNO:. REVISION NO., PAGENO.:
HNF-SD-CP-ATR-087 0 57 OF 67
Here’s what’s next.
This report can be searched. Note: Results may vary based on the legibility of text within the document.
Tools / Downloads
Get a copy of this page or view the extracted text.
Citing and Sharing
Basic information for referencing this web page. We also provide extended guidance on usage rights, references, copying or embedding.
Reference the current page of this Report.
Blackaby, W.B. PUREX exhaust ventilation system installation test report, report, October 7, 1997; Richland, Washington. (https://digital.library.unt.edu/ark:/67531/metadc687113/m1/59/: accessed June 20, 2019), University of North Texas Libraries, Digital Library, https://digital.library.unt.edu; crediting UNT Libraries Government Documents Department.