PUREX exhaust ventilation system installation test report Page: 5 of 80
This report is part of the collection entitled: Office of Scientific & Technical Information Technical Reports and was provided to Digital Library by the UNT Libraries Government Documents Department.
The following text was automatically extracted from the image on this page using optical character recognition software:
EUREX EXH SYSTEM ACCEPTANCE TEST PROCEDURE
Thd proper installation of the PUREX exhaust ventilation system components and wiring will be
sys ematically evaluated by performance of this procedure.
>er operation of PUREX exhaust fan inlet, outlet, and vortex damper actuators and limit switches
be verified, using special test equipment, to be correct and installed wiring connections will be
fled by operation of this equipment.
Thi test procedure will be performed entirely in the field and will not include any of the Surveillance
and Monitoring and Control System (SAMCONS) computer stations or equipment. -
I test is to be performed as a preliminary test to HNF-SD-CP-ATP-083, "PUREX Surveillance and
titoring and Control System (SAMCONS) Acceptance Test Procedure", where the damper actuator
t switches will be set for proper actuator stroke and actuators will again be tested, using manual and
matic computer control.
H-2-825909, "Instrumentation Loop Diagrams", Sheets 1 - 9
2.21 H-2-825910, "Instrumentation Logic Diagrams", Sheets 1 - 23
The following personnel will be required for the performance of this procedure:
" SAMCONS Cognizant Eneineer: The individual assigned direct responsibility for the
performance, preparation, and adequacy of the test.
" Test Director: The engineer assigned shift responsibility for performance of the test.
" Test Eneineer: The engineer assigned to assist and relieve the Test Director during the
performance of the test.
" Field Engineer (Field Personnel): A Test Engineer, Test Director, or Technician, and one
or more instrument technicians or electricians, assigned to direct/verify/conduct field
DOCUMENT NO:. : REVISION NO.: PAGENO.:
HNF-SD-CP-ATI-087 0 3 OF 67
Here’s what’s next.
This report can be searched. Note: Results may vary based on the legibility of text within the document.
Tools / Downloads
Get a copy of this page or view the extracted text.
Citing and Sharing
Basic information for referencing this web page. We also provide extended guidance on usage rights, references, copying or embedding.
Reference the current page of this Report.
Blackaby, W.B. PUREX exhaust ventilation system installation test report, report, October 7, 1997; Richland, Washington. (https://digital.library.unt.edu/ark:/67531/metadc687113/m1/5/: accessed June 26, 2019), University of North Texas Libraries, Digital Library, https://digital.library.unt.edu; crediting UNT Libraries Government Documents Department.