Date: February 22, 1949
Creator: Stanton, J.S.
Description: The attenuation of electro-statically and electro-magnetically shielded rooms in the ``E,`` ``R,`` ``I,`` and ``T`` Buildings was measured so that corrective measure could be taken if the attenuation was found to be low. If remedial measures could not be taken, the shortcomings of the rooms would be known. Also, the men making the measurements should oversee construction and correct errors at the time. The work was performed by measuring the attenuation at spot frequencies over the range of from 150 kilocycles to 1280 megacycles with suitable equipment mounted in small rubber-tried trucks. The attenuation was determined by ``before and after`` shielding and/or ``door open and door closed`` measurements after installation of copper shielding. In general, attenuation in the frequency range of approximately 10 to 150 mc. was good and was of the order expected. At frequencies in the range of 150 mc. to 1280 mc., the attenuation curve was more erratic; that is, at certain frequencies a severe loss of attenuation was noted, while at others, the attenuation was very good. This was mainly due to poor or faulty seals around doors and pass windows. These poor seals existed in the ``T,`` ``E,`` and ``I`` Buildings because the doors were ...
Contributing Partner: UNT Libraries Government Documents Department